Modbus Plus Converter
We have module solutions which allow integration directly into Modbus Plus as well as the stand alone solutions shown bottom right.
Download our Modbus for Field Technician for free, or purchase this guide for $20 on amazon.com.
Range of Conversion Solutions
Depending on project requirements select from units with varying resources and multi port devices. OEM and embedded solutions too.
|2x RS232 and 2x RS485
|FieldBus Support:eg Profibus, DeviceNet etcHot Standby Support
|10x RS232 and 2x RS485
|FieldBus Support: eg DH+, MB+, Profibus, DeviceNet etcHot Standby Support
|For Rockwell ControlLogix 5600
Lonworks and Fieldbus are options not proviced on base models.
FS30 series shown for purposes of illustration. Capability depends on hardware, firmware and configuration.
Supported Modbus Functions
01 Read Discrete Output Status (0xxxx)02 Read Discrete Input Status (1xxxx)03 Read Output Registers (4xxxx)04 Read Input Registers (3xxxx)05 Force Single Coil (0xxxx)06 Preset Single Register (4xxxx)15 Force Multiple Coils (0xxxx)16 Preset Multiple Registers (4xxxx)
Supported Data Types
16 Bit Integer Signed
16 Bit Integer Unsigned
32 Bit Integer Signed
32 Bit Integer Unsugned
32 Bit Packed Bit
8 Bit Packed Bit
4 byte FLoating Point Numbers
Scaling / Bit Packing
FieldServers can scale data and manipulate values using some binary logic and arithmetic functions. Scaling can be applied to each block of Modbus Data read / served.
- Move to change type : Convert from any FIeldServer Data Type to any other.
- Move to pack/unpack bits and bytes: It’s possible to address each bit in a 8,16 or 32 bit data element by using the packed data types.
- Move to change byte/word order: Handle the endianess of the remote system easily.
- Convert to/from Float, MK10, IEE754, 32 bit, 16 bit, 8 bit numbers
- Move conditionally:
- Perform Arithmetic Operation: + – * div sqrt, sqr ,
- Perform Binary Logic Operation: And, Or, Not, >, >= , <, <=
Most functions can be configured to occur on a configurable period or on update of the data source.
It’s possible to configure selected FiedlServer models to act in Hot Standby Mode. In one flavour of Hot Standby the two units are kept up to date all the time sharing the data from the field. In another mode, one unit is passive until it sees that the active unit is no longer responding.
FieldServer can easily be configured to allow a Modbus RTU client to talk to a ModbusTCP server and vice versa. You do not need to tell the FIeldServer which registers to map from one to the other. You simply conifgure the FieldServer telling it which port and protocol to use for each node.
Data Sheets and Manuals
Modbus Web Site: www.modbus.org
Need more info ? Call or email us.
Metasys® as used in this document is a trademark of Johnson Controls, Inc.